Haute couture switch range for trend setting eliteFind out more
Helping the mining industry grow in a sustainable wayExplore our solutions
Energy education from anywhere for efficiency everywhereBrowse our catalog
Your fastest way to answers!Download Mobile App
Issued to Schneider Electric South Africa (Pty) LtdDownload certificate
Schneider Electric South African Website×
To interlock the two Air Circuit Breakers (ACBs) with the same key, you need to order the Ronis keylock reference 48550 or Profalux keylock 48546.
For the Masterpact M, if there is already a keylock installed previously then you need to remove the old keylock from the adaptation kit and you should replace it with the new keylock.
For Masterpact NW you need to order the adaptation kit reference 48541.
1. The adaptation Kit 48541 comes without any keylocks, and you will have to order the keylocks as per the above reference provided.
2. The reference of the adaptation kit is the same for both types of keylock (either Ronis or Profalux).
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!