Haute couture switch range for trend setting eliteFind out more
Helping the mining industry grow in a sustainable wayExplore our solutions
Energy education from anywhere for efficiency everywhereBrowse our catalog
Your fastest way to answers!Download Mobile App
Issued to Schneider Electric South Africa (Pty) LtdDownload certificate
Schneider Electric South African Website×
The short-circuit current withstand rating (KA) of Tesys Comb Busbar is compatible with the breaking capacity of Motor Protection Circuit Breakers (MPCB) of GV series. The GV Series Comb Busbar does not have a conditional short-circuit current rating.
The maximum permissible peak current for GV2G*** Series Comb Busbar is 11KA and for GV3G*64 series Comb Busbar is 20KA.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!